The nitrogen generator is an important nitrogen production equipment used in various fields of industry. If the quality of the nitrogen generator is not good, it will affect the service life and production efficiency, increase the maintenance cost, and threaten people's health and safety. Machine repair and maintenance is particularly important, the following we will to talk about "Jiayu" nitrogen generator maintenance methods:
Jiangsu Jiayu CMS series pressure swing adsorption nitrogen generator
1) Install a regular drain on the sewage outlet of the air tank to reduce the load pressure of the treatment.
2) The normal use of equipment should pay attention to check whether each regular drain is drained normally, whether the air pressure meets 0.6Mpa or more, and whether there is a cooling effect by comparing the import and export of cold and dry machine, and check whether the nitrogen purity is stable.
3) The air filter must be changed every 4000 hours.
4) The activated carbon filter can effectively filter oil stains and can prolong the service life of molecular sieves. Activated carbon needs to be replaced once in 3,000 hours or 4 months.
5) Pneumatic valves for nitrogen generators, and one solenoid valve is recommended for each to prevent future problems.
Nitrogen Generator Maintenance Construction Site Guidance Procedures: Method for Maintenance of Nitrogen Generators.
1) Your company is responsible for on-site construction, personnel, various tools, pipelines, a set of components purchased by our company: transformation and maintenance of nitrogen generators, maintenance and repair prices of nitrogen generators, and maintenance cost of nitrogen generators.
2) Construction steps: simply clean the site, cut off the gas and power off, remove the adsorption tower head, remove all pipes of the nitrogen generator, remove all the waste from the adsorption tower, and clean it to check whether the flow plate at the top and bottom of the nitrogen adsorption tower is damaged. , repair if damaged. All pipelines should be purged with compressed air. Pneumatic valves should inspect the seals for damage. Severe replacement of pneumatic valves is required. The air treatment part filter was updated, and the activated carbon filter pipe was reconstructed synchronously. All work is completed, install all the pipelines and valves, ventilation power, sifting the whole pipeline system once, start to install carbon molecular sieves, start the nitrogen generator after the end of the loading, and check whether the nitrogen generators of each interface are leaky while checking. Nitrogen purity and capacity.
3) After the completion of all projects, on-site instructors will introduce the daily use and precautions to your company's responsible personnel.