The working principle of
Wet hot compressed air into the front cooler (high temperature) into the heat exchanger after heat and the cold air from the evaporator discharged heat, reduce the temperature of the compressed air into the evaporator.
After heat exchange of the compressed air flow into the evaporator through the evaporator of the heat transfer function and the refrigerant heat exchange, compression heat taken away by refrigerant in the air, compressed air cooling rapidly, moisture moisture in the air reaches saturation temperature rapid condensation, condensation water after coagulation form water droplets, high speed rotation after a unique gas water separator, moisture and air separation, because of the action of centrifugal force to separate water from the drain valve automatically after discharge. After cooling the air pressure dew point of the minimum of 2 ℃.
Cold air flows through the air cooled heat exchanger with high temperature and wet hot air inlet heat transfer, the heat exchange of the cold air by absorbing the heat up temperature of the inlet air, compressed air at the same time also passes refrigeration system of the secondary condenser (peer) unique design and high temperature of the refrigerant heat exchange again make exports is fully heated, ensure condensation of export air line. At the same time, it makes full use of the cold source of the exported air, which guarantees the condensation effect of the cooling system and ensures the air quality of the machine.